More A The pipe may be bent, but it is not intended for bending made at ambient temperature wherein the inside diameter of the bend is less than twelve times the outside diameter of the pipe being bent. The steel shall conform to the required chemical composition. Each length of pipe shall be subjected to a hydrostatic test without leakage through the pipe wall. As an alternative to the hydrostatic test, and when accepted by the purchaser, each pipe shall be tested with a non-destructive electrical method. Finally, flattening test shall be performed on the pipe in accordance with, electric-resistance-welded pipe, and furnace-welded pipe.
|Published (Last):||5 December 2011|
|PDF File Size:||9.86 Mb|
|ePub File Size:||19.70 Mb|
|Price:||Free* [*Free Regsitration Required]|
Full Description 1. Pipe having other wall thicknesses may be furnished provided such pipe complies with all other requirements of this specification and the outside diameter is as given in Table 2. Pipe ordered under this specification is intended for use in fire protection systems.
The pipe may be bent, but it is not intended for bending made at ambient temperature wherein the inside diameter of the bend is less than twelve times the outside diameter of the pipe being bent Note 2. C Not Schedule B Based on ft [6. Note 2-Successful bending of pipe is a function of equipment and technique as well as pipe properties.
See Table 1 for dimensions. See Table 2 for dimensions. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
Within the text, the SI units are shown in brackets. The values stated in each system may not be exact equivalents; therefore, each system shall be used independently of the other. Combining values from the two systems may result in non-conformance with the standard.
ASTM a 795 - Steel Pipe for Fire Protection
ASTM A135 Grade A/B welded pipes